notes for motor -杏鑫娱乐
1 before removal, to use compressed air to blow the motor surface dust, and wipe the surface dirt clean.
the choice of motor disassembly work site, clean up the site environment.
(3) familiar with motor structure characteristics and maintenance technical requirements.
(4) be prepared with tools (including specialized tools) and equipment needed for disassembly.
(5) in order to further understand the defects in the operation of the motor, if possible, can be done before the demolition of an inspection test.for this purpose, the motor should be tested with load, and the temperature, sound, vibration and other conditions of each part of the motor should be checked in detail, and the voltage, current, speed and so on should be tested. then the load should be disconnected, and a no-load inspection test should be done separately to measure no-load current and no-load loss, and the record should be made.
6 cut off the power supply, remove the external wiring of the motor, make a good record.
choose suitable voltage megohm meter to test the insulation resistance of the motor.in order to compare the insulation resistance value measured during the last maintenance and judge the trend of insulation change and insulation state of the motor, the insulation resistance value measured at different temperatures should be converted to the same temperature, generally converted to 75℃.
therefore, test absorption ratio k.when the absorption ratio is greater than 1.33, the motor insulation has not been affected by moisture or the degree of moisture is not serious.the absorption ratio measured at any temperature is also converted to the same temperature for comparison with previous data.